The Wine-Mate 1500SSW cooling unit is a split system design with a capacity of 150 cubic feet or approximately 800 bottles. With this split system, the condensing unit can be placed up to 50 feet away from the fan coil, and the cold air is fed into the cabinet or room (via the evaporator) through a copper pipe. The SSW series was designed to be wall-mounted and can be installed between two wall studs, making them an ideal choice for small and medium wine rooms.
Split System Wine Cooling Unit - wall mounted design
Outdoor enclosure is included with condensing unit
Fan Coil Specs: 115V / 60Hz, 0.35A, 26 lbs.
Fan Coil Dimensions: 16" W x 5.5" D x 36" H
Condensing Unit Specs: 115V / 60Hz, 3.1A, 30 lbs.
Condensing Unit Dimensions: 18" W x 12" D x 14" H
Coverage size: 150 cubic feet or approximately 800 bottles
Rated Capacity of 1900 BTU/hr
For Enclosure Up to 240 Cu. Ft. or Approximately 800 Bottles
Wall Mounted Design
Designed and Used to Provide a Stable Temperature Between 55°F~65°F for a Properly Insulated Room at a Normal Environment
Maintains Humidity of 50~70% RH Even When the Environment Becomes Dry or Humid
Temperature and Humidity Optimized for Long Term Storage of Wine, Fur and Tobacco
Condensing Unit Can Be Placed Away From the Wine Room as Far as 50 Feet, Which Will Bring an Extremely Quiet Operation
Uses Environmentally Friendly R134a Refrigerant
Copper Tubing Not Included
ETL and NSF Listed (Fancoil)
UL Listed (Condenser)
Warranty: 1-Year Parts and Labor
You may need to download Adobe Acrobat Reader to view and print PDF's. Click the link below to download Adobe Acrobat Reader for free. Download Adobe Reader
Wine Cellar Cooling Unit System (240 Cu.Ft. Capacity) Reviews
HUMIDITY & INSTALLATION: By the nature of their operation, wine cooling units will maintain a stable humidity level, lower than the relative ambient humidity. In situations where the ambient humidity is high, the cooling unit will lower the humidity to desirable storage levels. In situations where the ambient relative humidity is very low, the desired enclosure relative humidity may not be achieved without adding moisture. To add moisture to the enclosure only use slow, natural evaporation from a small porous water container. Do not use a humidifier.
TEMPERATURE & INSTALLATION: These wine cellar cooling units are designed to cool 25 degrees less than the ambient temperature of the venting side of the unit. In some cases, improper placement or installation may cause the unit's performance to be degraded. The condensing unit must have a constant supply of fresh air, less than 85 degrees F. If the condensing unit is located in a confined area with poor ventilation, the unit will not be able to reject the heat it is removing from the enclosure and a malfunctioning unit will be suspected, even though the unit is mechanically sound. Call us to discuss your installation concerns.