The CellarPro Mini-Split 4000S Wine Cellar Refrigeration System by CellarPro is designed for Wine Cellars up to 1000 Cu. Ft. The CellarPro Mini-Split is rated for both internal and external applications. This 1/3 Ton Nominal Refrigeration System allows for quieter operation by separating the Evaporator Unit from the Condensing Unit. In addition this 1/3 Ton Nominal Refrigeration System eliminates the need for large holes in your cellar wall.
The Evaporator Unit is designed to mount on the wall near the top of the Wine Cellar. Outside of the Wine Cellar, the Condensing Unit is attached to the Evaporator Unit by a Line-Set that can run up to 100 equivalent feet. The Line-Set is sold separately. The Evaporator Unit uses a variable-Speed Centrifugal Fan with three different settings including: (1) "High" - setting for maximum performance, and (2) "low" - for super-quiet operation.
The Condensing Unit is designed to handle environments ranging from 0°F to 110°F. The Condensing Unit requires 12 inches of unobsturcted space in front of the coils, and requires 600-700 CFM of ventilation when installed in a confined space.
This CellarPro Split Wine Cellar Refrigeration System offers a choice of wiring. The Condensing Unit can be either electronically controlled and wired to the Evaporator (single power source on the Evaporator Side), or it can be controlled by a Solenoid Valve (dual power source, one each to the Evaporator and Condensing Unit). Please Note: the former choice (Electronic Wiring) will allow the Condensing Unit to be used in temperatures down to -20°F.
For External Installations an Outdoor Hood is required.
For exposure to environments below 40°F, a Compressor Heater Modicifaction is required.
Access to the left and right side of the Evaporator Unit is required for installation.
All Split-Systems must be installed and charged on site by a Qualified HVAC Professional.
Line-Set equivalent feet must be calculated in accordance with ASHRAE Guidelines
To activate your warranty, you must complete and return an Installation Checklist.
Scroll down for details.
Up to 1000 Cu. Ft. Capacity (1/4 Ton Nominal)
Product Dimensions: 16.6W x 12.6D x 22.1"H
Engineered to operate in interior and external environments (0°F to 110°F)
For temperatures below 40°F a Compressor Heater modification is required
Schraeder Valve for Refrigerant Charge (R134A) and Superheat Adjustment
Multiple Knock-Outs and Access Points
Expansion Valve and Liquid Line Solenoid Valve (optional) come Factory Installed
Choice of Single or Dual Power Supplies for Evaporator and Condenser Units
Choice of Electronic or Valve Control for Condensing Unit
Evaporator and Condensing Unit are Factory Pressurized and Shipped with Dry Nitrogen
High-Performance Condensing Unit
Variable Speed Evaporator Fan for Super-Quiet Operation or Max Performance
Oversized Coated Evaporator Coils
Adjustable Humidity Control via Digital Display
1/2" ID Drain Line
53 Decibels at Low Fan Speed (Evaporator)
Electronic Thermostat, Digital LED Display and Audible/Visual Alarms
Sight Glass and Liquid Line Filter/Drier
Oversized Receiver for Long Line Sets
Line-sets can run up to 100 equivalent feet (and up to 30 vertical feet)
Adjustable Low Ambient Fan Cycling Control
Auto Reset High Pressure Switch
Compatible with a Dedicated 15-Amp Circuit
Optional Bottle Probe
Optional Outdoor Cover
ETL Tested and Certified (UL Standards) (PENDING)
Up to 1000 Cu. ft.
High Temperature Alarm
Digital Temperature Display
Condenser (Split Systems)
115V AC / 60Hz
Condensing Unit Cut Sheet
Evaporator Mounting Instructions
Line Sizing Chart
Wiring Diagram - Valve Control
Wiring Diagram - SIngle Power
Compressor Heater Evaluation
Specs & Features
You may need to download Adobe Acrobat Reader to view and print PDF's. Click the link below to download Adobe Acrobat Reader for free. Download Adobe Reader
Mini-Split Wine Cellar Refrigeration System (1000 Cu.Ft. Capacity) Reviews
Important Note about the CellarPro Split System Cooling Unit Warranty
Split systems cooling units are shipped in pieces that must be installed, connected and charged with refrigerant (R134a) by a properly trained technician.
Split systems are extremely advanced equipment, and can be damaged or destroyed if installed improperly. Common installation mistakes, which can cause irreparable damage to components in the condensing unit, include under or over charging the system, charging through the wrong valve, charging with impure refrigerant, etc.
Therefore, CellarPro requires a completed checklist from the installing technician in order to activate the manufacturer's warranty on this equipment. The checklist is located on the last page of the Owner's Manual. You can also find a .pdf version in the Info & Guides tab above.
Once CellarPro receives the checklist, they will review the data to make sure that the cooling system has been installed properly.
PLEASE NOTE: Your warranty will not be activated until the completed checklist is received. If the system malfunctions, CellarPro cannot provide assistance until they receive the completed checklist from the installing technician. If the unit is damaged because of improper installation, any repair or replacement parts and services will not be covered by warranty, and instead will be provided on a time and materials basis.
We make every effort to publish the checklist and the warranty policy so that it cannot be missed during the purchase process or by the installing technician. The warranty policy is posted online and is included in the Owner's Manual (which is shipped with the cooling system). The checklist is posted online, is included in the Owner's Manual, and is included as a separate, loose sheet with the cooling system's paperwork. In addition, 15 days after the order has shipped, CellarPro sends an email reminder stating that the checklist is required in order to activate the warranty. The email is sent to the dealer's email address, and to the "customer email" address provided by you at the time you place your order.
For the safety of the equipment and to activate the warranty, please make sure that you complete and return the checklist to us as soon as possible after their split system has been installed.
If you have any questions or need additional information, please don't hesitate to contact us.