CellarPro Mini-Split Wine Cellar Refrigeration System (1000 Cu.Ft. Capacity)
Designed for wine cellars up to 1000 cu.ft and rated for both internal and external applications
1/3 ton nominal refrigeration system allows for quiet operation and eliminates the need for large holes in your cellar wall
Variable-speed centrifugal fans have 3 settings, including "high" (maximum performance) and "low" (quiet operation)
Also features adjustable humidity control, electronic thermostat, and automatic defrost cycle
This wine cellar refrigeration system is ETL tested and certified (UL Standards [Pending])
INFO & GUIDES
The CellarPro Mini-Split 4000S Wine Cellar Refrigeration System by CellarPro is designed for Wine Cellars up to 1000 Cu. Ft. The CellarPro Mini-Split is rated for both internal and external applications. This 1/3 Ton Nominal Refrigeration System allows for quieter operation by separating the Evaporator Unit from the Condensing Unit. In addition this 1/3 Ton Nominal Refrigeration System eliminates the need for large holes in your cellar wall.
The Evaporator Unit is designed to mount on the wall near the top of the Wine Cellar. Outside of the Wine Cellar, the Condensing Unit is attached to the Evaporator Unit by a Line-Set that can run up to 100 equivalent feet. The Line-Set is sold separately. The Evaporator Unit uses a variable-Speed Centrifugal Fan with three different settings including: (1) "High" - setting for maximum performance, and (2) "low" - for super-quiet operation.
The Condensing Unit is designed to handle environments ranging from 0°F to 110°F. The Condensing Unit requires 12 inches of unobsturcted space in front of the coils, and requires 600-700 CFM of ventilation when installed in a confined space.
This CellarPro Split Wine Cellar Refrigeration System offers a choice of wiring. The Condensing Unit can be either electronically controlled and wired to the Evaporator (single power source on the Evaporator Side), or it can be controlled by a Solenoid Valve (dual power source, one each to the Evaporator and Condensing Unit). Please Note: the former choice (Electronic Wiring) will allow the Condensing Unit to be used in temperatures down to -20°F.
For External Installations an Outdoor Hood is required.
For exposure to environments below 40°F, a Compressor Heater Modicifaction is required.
Access to the left and right side of the Evaporator Unit is required for installation.
All Split-Systems must be installed and charged on site by a Qualified HVAC Professional.
Line-Set equivalent feet must be calculated in accordance with ASHRAE Guidelines
To activate your warranty, you must complete and return an Installation Checklist.
Scroll down for details.
Up to 1000 Cu. Ft. Capacity (1/4 Ton Nominal)
Product Dimensions: 16.6W x 12.6D x 22.1"H
Engineered to operate in interior and external environments (0°F to 110°F)
For temperatures below 40°F a Compressor Heater modification is required
Schraeder Valve for Refrigerant Charge (R134A) and Superheat Adjustment
Multiple Knock-Outs and Access Points
Expansion Valve and Liquid Line Solenoid Valve (optional) come Factory Installed
Choice of Single or Dual Power Supplies for Evaporator and Condenser Units
Choice of Electronic or Valve Control for Condensing Unit
Evaporator and Condensing Unit are Factory Pressurized and Shipped with Dry Nitrogen
High-Performance Condensing Unit
Variable Speed Evaporator Fan for Super-Quiet Operation or Max Performance
Oversized Coated Evaporator Coils
Adjustable Humidity Control via Digital Display
1/2" ID Drain Line
53 Decibels at Low Fan Speed (Evaporator)
Electronic Thermostat, Digital LED Display and Audible/Visual Alarms
Sight Glass and Liquid Line Filter/Drier
Oversized Receiver for Long Line Sets
Line-sets can run up to 100 equivalent feet (and up to 30 vertical feet)